Quabbin, Inc. diagnoses cause and provides components
Split stem guide bracket assembly by Quabbin, Inc.
Quabbin, Inc. was recently at the Aquarion Water Company in Greenwich, Connecticut, to diagnose the cause of and repair a leaky gate. With the repair over early in the day, the Facility Manager requested that a gate with a bent stem at Aquarion's nearby Cos Cob facility also be inspected. Quabbin, Inc. determined that the bent stem was due to a missing stem guide. A number of components were then manufactured to facilitate the repair of the Waterman gate. Parts included replacement extension and operator stems, thrust nut, coupling, four split stem guide bracket assemblies and a 5001.5 hoist with crank assembly. The existing pedestal was also modified, then blasted and re-powder coated, an economical way to provide many more years of use.
Posted: to General News on Fri, Jun 22, 2018
Updated: Fri, Jun 22, 2018